In this Reverse Osmosis (RO) Troubleshooting video we investigate why the RO System is off but still running and flowing water. There are a few areas to look at, including the Aquamatic Valves K524, along with the potential solenoid valve that is controlling it. We cover how to investigate the valve to see if it’s the solenoid or the valve that might have failed.
When the RO System is in the off position (no call for water) or the power is off to the Reverse Osmosis system then the Inlet valve should be shut not allowing water to flow through. This may not be the only source that could cause water to flow through the RO system. Such things as shared drain lines may be another cause or potentially the permeate line sits higher than the waste line. This can cause a vacuum when the RO is off and begin to siphon RO permeate water from the RO storage tank. It is recommended to install a vacuum breaker in the waste line (at the highest point)
Is your RO System still running? Need RO Service Now?
Contact The Service Team (855) 787-4200 firstname.lastname@example.org
28 Year Of Water Treatment Equipment Experience. I have been blessed with the opportunity to learn from the ground up. Starting in the water treatment field as a service technician. Servicing all major brands of water treatment equipment. Give Us A Call (855) 787-4200 or Email email@example.com