In this video, we showcased a Reverse Osmosis Housing Replacement on a Pro-100-NA and Pro-150-NA Reverse Osmosis System. The housings that were replaced were wave cyber 8″ Reverse Osmosis Housings (RO Housings). The project entailed replacing (6) Housings Some of the housings were longer than others. The water system was used to provide purified water for both Boiler Feed Water Applications and Process Applications in a manufacturer located in Montana.
Things to take into consideration when replacing these housings:
1.) Grooved Clamps – Recommended to replace the grooved clamps & gaskets
2.) Piping – Bring some PVC as the permeate ports may not line up and may require some rebuilding, same with the concentrate.
3.) Membranes – During this housing replacement we replaced the RO membranes. Which is a perfect time to do it as the new housing will be empty.
PRO Reverse Osmosis Manuals – https://bit.ly/32LUqLB
PRO Reverse Osmosis Drawings – https://bit.ly/3qzLNMp
RO Troubleshooting Guide – https://bit.ly/3FIYHif
RO Membranes & Filters – https://bit.ly/2Ynfnua
Need Help with Reverse Osmosis Housing Replacement? – Contact One Of Our RO Experts – https://bit.ly/3h3a6hN
27 Year Of Water Treatment Equipment Experience. I have been blessed with the opportunity to learn from the ground up. Starting in the water treatment field as a service technician. Servicing all major brands of water treatment equipment.