Plastic Molding Equipment: Water Scale
Complete Water Solutions was called out to a plastic mold facility after a new extrude machine scaled up due to hard water. The scale caused thousands of dollars of downtime. Complete Water Solutions did a full audit of the facility and found that hard water and the lack of adequate chemical treatment was causing the issue.
In this process achieving 0 PPM hard water is critical. The main softener system was not able to achieve this due to variances in the incoming water. The recommendation was to install a polishing water softener system.
Complete Water Solutions selected a Fleck 2900 Single Metered Softener System. Complete Water Solutions provided a full turnkey operation including piping.
To Learn More About Reducing Scale Build Up In Your Injection Mold or Form Molding Process Contact Complete Water Solutions (855) 787-4200 or email@example.com
28 Year Of Water Treatment Equipment Experience. I have been blessed with the opportunity to learn from the ground up. Starting in the water treatment field as a service technician. Servicing all major brands of water treatment equipment. Give Us A Call (855) 787-4200 or Email firstname.lastname@example.org