Recently Complete Water Solutions received a call regarding spotting on a paint line. This current customer uses RO Water to rinse the final product prior to boxing and shipping the products to their customers. The customer had not had much experience with Reverse Osmosis & Softener systems so Complete Water Solutions performed a “Free Preventative Maintenance Check-Up” on the system and found the reason for their problems.
Preventative Maintenance Inspections & Repairs
Once the free preventative maintenance inspection was performed we found that the softeners had quit working. The softeners were producing hard water which resulted in scaling of the RO membranes. This scale resulted in increased conductivity and hard water bleed through. That ultimate result was spotting on the products coming off the rinse line. Complete Water Solutions, after talking with the customer, found that it was better to just replace the softener due to the age of the equipment and the fact that some of the parts had become obsolete.
28 Year Of Water Treatment Equipment Experience. I have been blessed with the opportunity to learn from the ground up. Starting in the water treatment field as a service technician. Servicing all major brands of water treatment equipment. Give Us A Call (855) 787-4200 or Email firstname.lastname@example.org