Complete Water Solutions recently changed out Nano Filtration Membranes on a Osmonics Beverage Nano Filtration Unit. The system was experiencing high conductivity. During the change out service plastic pieces / debris was found in the RO membranes. Upon future investigation it was noted that the pump had broken impellers that caused the plastic shards to end up in the filters.
Prior to changing out the filters the water system was evaluated:
Membrane feed 33psi
Permeate conductivity 200ms
Concentrate conductivity 273.7
After changing out the filters the water system was re-evaluated:
Membrane feed 156.5psi
Concentrate 123.4 psi
Concentrate 42gpm gpm
Permeate conductivity 22.9ms
Concentrate conductivity 307.6
Need Your Beverage Reverse Osmosis System Evaluated Or Need Membranes?
Contact Complete Water Solutions (855) 787-4200 email@example.com
27 Year Of Water Treatment Equipment Experience. I have been blessed with the opportunity to learn from the ground up. Starting in the water treatment field as a service technician. Servicing all major brands of water treatment equipment.