CWT-3000-4” Triplex Industrial Softener System (400 GPM Softener System)
Complete Water Solutions supplied a triple tank softener system. The Industrial Water Softener comprised of (3) 72” Diameter x 72” Tall side shell. Each vessel was epoxy lined interior and polyurethane exterior coating. The reason the exterior coating was selected is to help with exterior environment corrosion. Vessels were 100 PSIG Non-Code. Each vessel contained 102 cubic feet of Dow Cation Resin Amberlite HPR 1100 Na (formally Dowex Marathon C)
Softeners utilized Promag 300 Flow Meters. The capacity of each softener vessel is 3,000,000 grain capacity based off of max salt dosage. The softener uses signals from a flow totalizer to initiate the automatic regeneration. Regeneration may also be initiated manually by an operator or by hardness monitor.
The valves are pneumatically controlled by individual solenoid valves. Each softener vessel has a Nema 4X enclosure to house the solenoid valves that control the valve operation. The softener main controller is a PLC system equipped with a Allen Bradley 1400 Micrologix and AB HMI
The hardness monitors selected for this project were waltron.
|System Design Flow Rate||945 GPM Normal 1200 GPM Peak|
|Operating Water Pressure||40-100 PSIG|
|Operating Water Temperature||100°F Maximum|
|Normal Flow Rate & Pressure Loss @ 60°F||315 GPM @ ≤6 PSID|
|Peak Flow Rate & Pressure Loss @ 60°F||400 GPM @ ≤8 PSID|
|Minimum Flow Rate||56 GPM|
|GPM/SQ. FT., Design||11.3 @ Normal Flow 14.4 @ Peak Flow|
|Backwash Rate @ 60°F||140 GPM|
|Ion Exchange Capacity||3,000,000 @ 15# NaCl/cu.ft. resin dosage 2,000,000 @ 6# NaCl/cu.ft. resin dosage|
Need A Softener? Call Or Email Us For Your Next Softener Project (855) 787-4200 email@example.com
27 Year Of Water Treatment Equipment Experience. I have been blessed with the opportunity to learn from the ground up. Starting in the water treatment field as a service technician. Servicing all major brands of water treatment equipment.