Complete Water Solutions was called out a power plant recently due to finding resin in its drain line and in the RO System. Complete Water Solutions arrived onsite and inspected every softener system to determine which unit was causing the problem.
After further inspection, Complete Water Solutions was able to find the problem and fix the Industrial Softener System. Complete Water Solutions fixed the upper distributor system in the softener system. We replaced it with a more robust distributor that is supported by the bottom of the tank.
Complete Water Solutions pulled all the butterfly valves, inspected all the drains and verified all the repairs.
Complete Water Solutions pulled a core sample of softener resin and tested it, we topped off the resin that was lost.
We were able to make all the repairs without shutting down the entire system!
Need help with your industrial water softener? Contact Complete Water Solutions today!